AFBC BOILER LIGHT UP PROCEDURE PDF
Requirements of Bed material,Charcoal & Diesel. Bed material Maximum Particle size Bulk density Chemical composition MM TO The start up of fluidised bed combustion boilers has always been a subject of the most process of raising bed temperature above °C. In the process of. boilers/heaters is the concept of Fluidised Bed Combustion (FBC). A descriptive feature for Start up/ Firing Procedure for AFBC boiler/heater bed. Initially.
|Published (Last):||2 May 2006|
|PDF File Size:||6.93 Mb|
|ePub File Size:||14.88 Mb|
|Price:||Free* [*Free Regsitration Required]|
Check the following equipments for adequate lubrication. Feed control valve and its bypass valve. Set the air flow to MM of wc P. All interlocks to be cross checked.
Drain valves of water level gauge. Turn off the oil burners and remove from furnace. Valves before and after feed control valve in feed line.
CFBC boiler operation procedure? Inspect the boiler before start and check Manual on Boiler Tube Fluidized bed combustion – wikipedia, the free encyclopedia Fluidized bed combustion FBC is a combustion technology used to burn solid fuels.
C and start the ash handling system.
Afbc Boiler Light Up Procedure
Once fludisation study is completed boiler is ready for light up. C and stable the boiler. Cfbc boiler operation procedure? Check the following valves are kept in open condition. Initally the top bed temperature will raise and at the time of mixing temperature drops and bottom temperature raises at the time of mixing. Ensure the deaerator water level as normal. Keep the PA lines clear and take trial run of feeder of first compartment. After stabilisation of bed temperatures stop the burners and LDO pumps.
Shiatsu Massage Manual Afbc boiler boiler, The Fuel feeders and controllers. Maintain drum level at normal recommended level.
Afbc Boiler Operation Manual – ante-annum. Light up all the four burners. Close the bed superheater drains. Measure air box pressure P1 MM of wc 3. Drum and main line vent.
Start up vent valve. Check for dry fuel MM is available in bunker and gates below bunker are open and fuel is available at feeder inlet. Afbc Boiler Operation Manual – snowman-ro.
AFBC ( Atmospheric Fluidized Bed Combustion ) BOILER COLD START UP PROCEDURE – ASKPOWERPLANT
Check the following valves in boiler are in closed condition. Boiler Manual For Cfbc – boiler operation agbc Add gas plenum pressure P2 Furnace draught to P1.
When the bed temperatures reaches Deg C start the drag chain coal feeder.
Afbc Boiler Light Up Procedure
Inspect the boiler before start and check Manual on Boiler Tube Bhel steam generators products afbc boilers Tags: Afbc Boiler Operation Manual – boiler operation procedure 1 seminar afbc boiler operation procedure,Ask Latest information,Abstract,Report,Presentation free download cfbc Documents.
Boiler Installation – Afbc Documents.
Main steam stop and pilot valve. Bed material to be filled and level of defluidised bed should be MM of WC. A fixed quantity of diesel wetted Charcoal 40 Kgs is spread uniformly over the compartment.
Feed pump and drives. Valves on feed line connecting to feed pumps operation. Check the bed material and fludisation study is being done.