AFBC BOILER LIGHT UP PDF
Tags: HOT START UP AFBC BOILER, light up of afbc boiler, WARM In this article we discussed about the AFBC boiler hot startup and cold. The start up of fluidised bed combustion boilers has always been a subject of the most surface, it is advised not to proceed with the light up. Unless the top. Requirements of Bed material,Charcoal & Diesel. Bed material Maximum Particle size Bulk density Chemical composition MM TO
|Published (Last):||13 August 2016|
|PDF File Size:||4.23 Mb|
|ePub File Size:||19.10 Mb|
|Price:||Free* [*Free Regsitration Required]|
Bed super heater drains.
AFBC BOILER HOT/WARM STARTUP PROCEDURE – ASKPOWERPLANT
Published on Oct View 3. Ensure feed water flow through economiser at the time of light up to avoid steaming of economiser. The pressure drop across bed is obtained for various air flow. Afbc Boiler Operation Manual – boiler operation manual at Bed material Maximum Particle size Bulk density Chemical ljght The air flow at which fludisation starts is noted and will be maintained at the time of mixing.
Afbc Boiler Operation Manual – boiler operation procedure 1 seminar afbc boiler operation procedure,Ask Latest information,Abstract,Report,Presentation free download cfbc Documents. Feed pump and drives.
Afbc Boiler Operation Manual – snowman-ro. All interlocks to be cross checked. Valves on feed line connecting to feed pumps operation.
A fixed quantity of diesel wetted Charcoal 40 Kgs is spread uniformly over the compartment. Start the LD oil pump and maintain the oil pressure between 6. Once fludisation study is completed boiler is ready for light up.
Check the following valves are kept in open condition. C and stable the boiler.
Afbc Boiler Light Up Procedure
Start up vent valve. Inspect the boiler before start and check the following 1.
Valves before and after feed control valve in feed line. Close the bed superheater drains. Boiler light up procedure A fixed quantity of dry charcoal Kgs i.
Afbc Boiler Operation Manual – ante-annum. Ensure all equipment trial to be taken. Main lught stop and pilot valve. Cfbc boiler operation procedure? Check the following equipments for adequate lubrication. Check for dry fuel MM is available in bunker and gates below bunker are open and fuel is available at feeder inlet.
AFBC ( Atmospheric Fluidized Bed Combustion ) BOILER COLD START UP PROCEDURE – ASKPOWERPLANT
Initally the top bed temperature will raise and at the time of mixing temperature drops and bottom temperature raises at the time of mixing. After stabilisation of bed temperatures stop the burners and LDO pumps. Shiatsu Massage Manual Afbc boiler boiler, The Ensure the deaerator water level as normal. Start the FD fan and maintain bed pressure mmwc. Keep the PA lines clear and take trial run of feeder of first compartment. Ensure all personel were cleared.
Inspect the boiler before start and check Manual on Boiler Tube Bhel steam generators products afbc boilers Tags: